Click on “Download PDF” for the PDF version or on the title for the HTML version.
If you are not an ASABE member or if your employer has not arranged for access to the full-text, Click here for options.
Greenhouse Dehumidification Requirement in Cold Regions
Published by the American Society of Agricultural and Biological Engineers, St. Joseph, Michigan www.asabe.orgCitation: 2012 Dallas, Texas, July 29 - August 1, 2012 121337447.(doi:10.13031/2013.42153)
Authors: Jingjing Han, Huiqing Guo, Robert Brad, Doug Waterer, Zhu Gao, Rick VanDuyvendyke
Keywords: Greenhouse dehumidification, moisture balance model, experimental measurement model, refrigeration dehumidifier, air-to-air heat exchanger, cold regions
Dehumidification is essential for greenhouse humidity control due to the serious effect of high relative humidity on crops. A few dehumidification methods have been tested in a greenhouse. Mechanical refrigeration dehumidification is proved to be the most energy efficient and is the most promising method for greenhouses in cold regions. However, limited information exists on how to quantify the dehumidification requirement of a greenhouse. In this study, two methods, a moisture balance modeling method and an experimental measurement method, were employed to estimate the dehumidification needs of a commercial greenhouse. Experimental data collected from the same greenhouse with three dehumidification treatments, i.e. mechanical dehumidifiers, air-to-air heat exchangers, and temperature controlled ventilation with exhaust fans, were used to verify the predicted results of the two methods. The results revealed that compared with the moisture balance modeling, the experimental method was proved to be more accurate to estimate the greenhouse dehumidification. A more complete moisture balance model should be developed in the future.(Download PDF) (Export to EndNotes)