Click on “Download PDF” for the PDF version or on the title for the HTML version.
If you are not an ASABE member or if your employer has not arranged for access to the full-text, Click here for options.
Water Use by Greenhouse Evaporative Cooling Systems in a Semi-Arid Climate
Published by the American Society of Agricultural and Biological Engineers, St. Joseph, Michigan www.asabe.orgCitation: 2007 ASAE Annual Meeting 074013.(doi:10.13031/2013.23054)
Authors: Nadia C Sabeh, Gene A Giacomelli, Chieri Kubota
Keywords: pad-and-fan, high-pressure-fog, ventilation, water use efficiency, controlled environment
Water availability is a common concern in semi-arid regions, such as Southern Arizona, USA, where greenhouse crop production is popular due to high solar radiation. Hydroponic greenhouse crop production greatly reduces irrigation water use; however, water use by evaporative cooling systems has never been quantified. This project investigated water use by two evaporative cooling systems: pad-and-fan (P&F) and high-pressure-fog (HPF) with fan ventilation and a central overhead line. Water use data were collected from a double-layer polyethylene film-covered greenhouse (28 x 9.8 x 6.3 m) with mature tomato plants (1.7 plants m-2) from 08:00 – 17:00 for each ventilation rate tested under semi-arid climate conditions (TOut,Avg=35°C, RHOut,Avg=10%, SolarAvg=900 W m-2). Total daily water use by P&F was 3.2, 6.4, 8.5, and 10.3 L m-2 for ventilation rates of 0.016, 0.034, 0.047, 0.061 m3 m-2 s-1, respectively. Total daily water use by the HPF system was 7.9, 7.4, and 9.3 L m-2 for fan ventilation rates of 0.01, 0.016, 0.034 m3 m-2 s-1, respectively. Total greenhouse WUE (water use efficiency) was calculated using hydroponic irrigation (4.5 L m-2) and evaporative cooling water use. Total WUE values were comparable to sprinkler-irrigated WUE (15-19 L m-2) and flood-irrigated WUE (< 12 L m-2). Using a “closed” hydroponic irrigation system would increase the WUE greatly and should be implemented to conserve water. Furthermore, HPF water use should decrease under natural ventilation.(Download PDF) (Export to EndNotes)