Click on “Download PDF” for the PDF version or on the title for the HTML version.
If you are not an ASABE member or if your employer has not arranged for access to the full-text, Click here for options.
Fogging Systems for Cooling Greenhouses
Published by the American Society of Agricultural and Biological Engineers, St. Joseph, Michigan www.asabe.orgCitation: Paper number 034041, 2003 ASAE Annual Meeting . (doi: 10.13031/2013.13859) @2003
Authors: A. Arbel, M. Barak, A. Shklyar
Keywords: Fogging system, Forced Ventilation, Climate Control, Uniform Conditions
This work focuses on development of the fogging system mathematical model, and the operational characterization of the fogging system in combination with forced ventilation for cooling greenhouses. The cooling system was installed and operated according to the following scheme: high-pressure spray nozzles with the highest possible uniformity of distribution, fans at both ends of the greenhouse (north & south) were placed at ground level, roof openings and two side openings (east & west). The results obtained revealed that inside the greenhouse air temperature and relative humidity of 28oC and 80% respectively, were maintained during the summer at midday and generally high uniformity of the climatic conditions (the same magnitude of temperature measurements error 0.5C), within the greenhouse, in the lengthwise (north-south) and vertical directions. In contrast to that, there was significant variation across the width of the greenhouse (east-west), which arose as a result of wind action; however, under the conditions of a greenhouse with developed plants or with the windward openings closed, uniform conditions were obtained. It must be concluded that in order to obtain completely uniform climatic conditions throughout the volume of the greenhouse, it is desirable to install fans in all four sides. Such an arrangement may makes possible: uniform climatic conditions within the desired range, even in the summer months; good control over the climatic conditions through reduction of the influence of the wind; operation of the greenhouse by means of a relatively simple control system; the establishment of greenhouses in large units and, consequently, better exploitation of the land area and significant reduction in the cost per unit area of the structure.(Download PDF) (Export to EndNotes)